Release #13-064 Firm’s Recall Hotline: (855) 779-9200
CPSC Recall Hotline: (800) 638-2772
CPSC Media Contact: (301) 504-7908
The valves can crack and cause gas to leak. This poses fire and explosion hazards.
Fu San Machinery Recalls Low Lead Ball Valves Installed in Flammable Gas Lines Due to Fire and Explosion Hazards
WASHINGTON, D.C. – The U.S. Consumer Product Safety Commission, in cooperation with the firm named below, today announced a voluntary recall of the following consumer product. Consumers should stop using recalled products immediately unless otherwise instructed. It is illegal to resell or attempt to resell a recalled consumer product.
Name of Product: Low Lead Ball Valve/Shut-Off Gas Valves
Units: About 163,000
Importer/Distributor: Aqualine, of Corona, Calif.; AY McDonald Manufacturing Co., of Dubuque, Iowa; FNW, of Portland, Ore.; Hodes Co., of Kansas City, Mo.; Legend, of Auburn Hills, Mich; Leonard Valve, of Cranston, R.I. and Mueller of Memphis, Tenn.
Manufacturer: Fu San Machinery Co. Ltd., of Taiwan
Hazard: The valves can crack and cause gas to leak. This poses fire and explosion hazards.
Incidents/Injuries: None reported.
Description: This recall involves seven brands of sweat and threaded, low lead ball valves used in flammable gas piping systems used in commercial or residential settings. They are brass shut-off valves assembled with pipe lines of 3/4 inch and 1 inch and have a date code 1103 through 1112, in YYMM format, where YY is the year and MM is the month. The date code is located under the valve handle. The pipe size is marked on the body of the valve. Fu San’s logo and the “O” marking designated for low lead valves are marked on the valves’ neck under where the handle assembles. The word “Taiwan” appears on the handle as a country of origin marking. The valves were sold under the following brand names and model numbers:
Brand Name | Model Number | Valve Dimensions/Sweat or Threaded Valves
Aqualine | BBV-075-LF | 3/4 inch/Threaded
Aqualine | BBV-075S-LF | 3/4 inch/Sweat
Aqualine | BBV-100-LF | 1 inch/Threaded
Aqualine | BBV-100S-LF | 1 inch/Sweat
AY McDonald | 72032S | 3/4 inch/Sweat
AY McDonald | 72032T | 3/4 inch/Threaded
FNW | FNWX410AF | 3/4 inch/Threaded
FNW | FNWX410AG | 1 inch/Threaded
FNW | FNWX411F | 3/4 inch/Sweat
FNW | FNWX411G | 1 inch/Sweat
Hodes Co. | 40-642 | 1 inch/Threaded
Hodes Co. | 40-662 | 1 inch /Threaded
Hodes Co. | 40-677 | 3/4 inch/Sweat
Hodes Co. | 40-687 | 3/4 inch/Sweat
Hodes Co. | 40-678 | 1 inch/Sweat
Hodes Co. | 40-688 | 1 inch/Sweat
Legend | T1002NL | 1 inch/Threaded
Leonard Valve | 83503 | 3/4 inch/Sweat
Leonard Valve | 83504 | 1 inch/Sweat
Leonard Valve | 83538 | 3/4 inch/Threaded
Leonard Valve | 83539 | 1 inch/Threaded
Mueller 107-844NL | 3/4 inch/Sweat
Sold by: Fu San Machinery directly to seven distributors nationwide from April 2011 through January 2012 for between $13 and $20.
Manufactured in: Taiwan
Remedy: Consumers should turn off the gas supply until a replacement gas valve has been professionally installed. Consumers should contact Danville Sales which, on behalf of Fu San Machinery, will provide compensation of $300 to reimburse customers for costs incurred to remove and return the valve and for purchasing and installing a replacement valve. The affected valve should be returned to the Danville Sales Office for Fu San Machinery with a photo depicting the valve in the gas line before removal and showing the date code on the valve, along with the address and details of the location where the valve was installed. The requested information, the recalled valve, and the consumer name and address should be sent to the address in the Consumer Contact paragraph. Upon receipt, Fu San will reimburse customers in the amount of $300.
Consumer Contact: Danville Sales Office for Fu San Machinery, 1101 N. Kings Hwy, Cherry Hill, NJ 08034; toll-free at (855) 779-9200, from 9 a.m. to 5 p.m. ET Monday through Friday, or online at www.fsvalve.com.tw, then click on the Safety Recall Notice button for more information.
To see this recall on CPSC’s web site, including pictures of the recalled product, please go to: http://www.cpsc.gov/cpscpub/prerel/prhtml13/13064.html